The overload relay is wired in series with the motor, so the current that flows to the motor when the motor is operating also flows through the overload relay. It will trip at a certain level when there is excess current flowing through it. This causes the circuit between the motor and the power source to open.
How does the overload relay protect the motor?
Overload relays protect a motor by sensing the current going to the motor. … When current is too high for too long, heaters open the relay contacts carrying current to the coil of the contactor. When the contacts open, the contactor coil de-energizes, which results in an interruption of the main power to the motor.
What is the main function of overload relay?
Overload relays cut off current to the motor when a high-current situation develops due to a ground fault, short circuit, phase failure, or mechanical jamming. They are an inexpensive way of avoiding downtime for repair or replacement of failed motors from excessive current.
What is the function of overload relay in motor control circuit?
An overload relay is a device that protects an electric motor against overloads and phase failure. It senses overloading of motor and interrupts the power flow to the motor, thus protecting it from overheating and winding damages.
How do I know if my overload relay is bad?
Unplug the start relay from the compressor and give it a shake. If you can hear rattling on the inside of the start relay, then the part is bad and will have to be replaced. If it’s not rattling and appears to be in good condition, you may have a problem with the actual compressor.
How do you adjust a motor overload relay?
Thermal Overload Relay setting = 100% x Full Load Current (Line).
- Thermal Overload Relay setting = 100% x Full Load Current (Line).
- Thermal Overload Relay setting = 100%x6 = 6 Amp.
What are the basic requirements of an overload relay?
An overload relay has two basic parts:
- A heater element that is connected in series with the power line to the motor. …
- A set of normally closed contacts that are connected in series with either the lines feeding the motor (manual starters) or the coil of the magnetic contactor (magnetic starters).
What must be done before a motor overload can be reset?
the overload relay cannot be reset until the overload heater has cooled. The overload relay is reset by first turning the starter all the way off and then turning it back on.
What happens when a motor is overloaded?
Motor overload occurs when a motor is under excessive load. … Excessive motor heat is a major cause of motor failure. In the case of an overloaded motor individual motor components including bearings, motor windings, and other components may be working fine, but the motor will continue to run hot.
Do all motors need overload protection?
Most other continuous duty motors having a marked service factor of not less than 1.15 or, with a marked temperature rise not over 40 degrees Celsius, are required to have overload protection rated at 125 percent of the motor nameplate full-load current rating.
What are 2 types of overload relays?
There are three types of thermal overload relays — bimetallic, eutectic, and electronic. Bimetallic thermal overload relays (sometimes referred to as heater elements) are made of two metals, with different coefficients of thermal expansion, that are fastened or bonded together.
How do you test a motor overload relay?
Overload Protection Test:
- Measure the normal motor running current (i motor).
- Turn off the motor and let it cool for about 10 minutes.
- Calculate the following ratio: i (motor) / i (overload min FLA). …
- Set the overload to its minimum FLA and turn on the motor.
- Wait for the overload to trip.
How do you test an overloaded switch?
Touch the leads on your digital multimeter to both sides of the thermal overload switch. Watch the needle on the digital multimeter display to determine if your thermal overload switch needs to be replaced. A functional thermal overload switch will cause the needle to move to “0”.
How do you test circuit overload?
Signs of Overloaded Circuits
The most obvious sign of an electrical circuit overload is a breaker tripping and shutting off all the power. Other signs can be less noticeable: Dimming lights, especially if lights dim when you turn on appliances or more lights. Buzzing outlets or switches.