How do you check windings on a 3 phase motor?
Check the motor winding resistance or ohms reading using a multimeter or ohmmeter for phase to phase terminal ( U to V,V to W ,W to U ). The ohms reading for each winding must be the same (or nearly the same). Remember that the three phases have identical windings or nearly so!
How do you check motor windings with a multimeter?
Inspect the Motor Windings With a Multimeter
To begin, set the multimeter to read ohms and then test the motor’s wires and terminal.
How do I know if my 3 phase motor is bad?
Check all three wires singly T1,T2,T3 (all three phases) to the ground wire. Readings should be infinite. If its zero or reads any continuity at all, then a problem exists with either the motor or cable . If it is go directly to the motor and disconnect from cable and check motor and the cable separately.
How do you check motor windings?
Set your multimeter to Ohms. Start by completely disconnecting the spindle motor from all power sources. Check each wire, including T1, T2, T3 and the ground wire. If the reading is infinite, your motor should be fine.
How do you know if your motor windings are bad?
With a multimeter set to low ohms (usually 200), test between each winding terminal and the metal casing of the motor. If there is any reading on any of these then the motor is bad, do not use it. You may find that when it runs ungrounded that the casing becomes live at up to supply voltage.
How many ohms should a 3 phase motor read?
The reading should be between 0.3 to 2 ohms. If it is 0, there is a short. If it is over 2 ohms or infinite, there is an open. You can also dry the connector and retest to possibly get more accurate results.
Should motor windings have continuity?
The windings (all three in a three-phase motor) should read low but not zero ohms. … It will usually be low enough (under 30 Ω) for the audible continuity indicator to sound. For proper motor operation, all windings must have megohm readings to ground, i.e. to the motor enclosure.
How do you find the insulation resistance of a 3 phase motor?
Phase Resistance: Take the insulation tester and set it to 500V. Take each end and place it on different permutations of L1, L2 and L3 and record each reading. Phase to Earth Resistance: Take the insulation tester, using the same setting, and check each lead from phase to the frame of the motor.
What is a good megohm reading for a motor?
The rule may be stated: Insulation resistance should be approximately one megohm for each 1,000 volts of operating voltage, with a minimum value of one megohm. For example, a motor rated at 2,400 volts should have a minimum insulation resistance of 2.4 megohms.